Oct 29, 2011· A/C Condenser fan motor wiring. I have an A/C condenser. I have an A/C condenser fan motor that has four wires coming out of it. The wires are brown, brown with a white stripe, purple and black. I am replacing the condenser fan motor and the new motor has red, purple, black, and brown wires. I have NOT unplugged the OLD wires (motor) from .
Apr 25, 2010· If you are sure of the voltage then you would wire black to one leg of the contactor, white to the other leg of the contactor and then if you want to simplify the wiring you can run a separate capacitor which would only have two terminal connections on it.This is where you put the brown and the brown/wht. wire one on either side of the new .
May 14, 2012· how wire a fan condenser motor with black, white, brown and brown/wuite wires my fan condenser motor broke and the - AO Smith A.o. Smith Orm5458 1/3 A 1/6 question. Search Fixya. Browse Categories Answer Questions . AO Smith A.o. Smith Orm5458 1/3 A 1/6 Hp, 1075 Rpm Rpm, 1075 Volts Volts, 2 . Wiring a fan motor to a dual capacitor, the leads .
Aug 21, 2019· How to wire a condensing fan motor for 3 vs. 4 wires is a common question by new techs. Jesse Grandbois submitted this tech tip to help make it simple. Thanks, Jesse!. This is a quick one on the difference between wiring universal condenser fan motors and why brown+white is the same wire as white. This one […]
May 24, 2018· Simply put, no – you did not buy the wrong condenser fan motor. While most original condenser fan motors only have three wires, it's very common for replacement condenser fan motors to have four. This guide will explain how to wire your new condenser fan motor using a four wire setup or a three wire setup when using a single run capacitor .
Hello, I have an A.O. Smith Condenser Motor and told this was the correct replacement. The old motor is 3-wire and the new motor is 4-wire. I have attached images. Can someone please explain which wires on the new motor go to the old connections. This is an image of the Wiring Schematic on the old motor 2013-05-01_15-37-26.jpeg - EmmMay's library This is an image of the wiring schematic on the .
How to Wire a Run Capacitor to a Motor | Blowers & Condensers – Sometimes when a blower or condenser fan motor goes bad a technician or even a DIYer has issues wiring the new motor and capacitor.Most motors come with clear instructions or a wiring diagram on the side, however, some people still struggle with the wiring part of the motor to the capacitor.
Sep 08, 2007· So I generally install a new cap for just the fan motor and wire it up like you did today. And another thing to keep in mind is if the capacitence ratings were the same you could connect black to the contactor, yellow to common on the capacitor, and brown to fan on capacitor, and cap off the brown and white wire.
Change 4 wire condenser motor to 3 wire motor The one I am taking out is a 230 volt it has 2 brown capacitor wires and a black and white. The one I want to put in is a 230 volt/5 mfd capacitor motor.
Your old motor had 3 wires. FYI: The old capacitor has 3 connections, HERM (hermetically sealed compressor), C (common), and F (fan). The old motor had a white wire (or purple) that went to the old capacitor marked C (for common), the black wire to the contactor (for hot) and the brown wire to the F …